Application of Fractal Theory in Brick-Concrete Structural Health Monitoring ()

Changmin Yang^{1}, Xia Zhao^{2}, Yanfang Yao^{2}, Zhongqiang Zhang^{1}

^{1}Architectural Engineering Institute, Hebei University, Baoding, China.

^{2}Hebei College of Science and Technology, Baoding, China.

**DOI: **10.4236/eng.2016.89058
PDF HTML XML
1,177
Downloads
1,806
Views
Citations

In order to monitor and forecast the deformation of the brick-concrete building, by taking a brick-concrete building as research object, fiber grating sensors were used to collect the monitoring data and double logarithmic curve of limit value characteristic and monitoring data were obtained based on the fractal theory. Constant dimension fractal method cannot be used to analyze the data directly. With the method of variable dimension fractal, we accumulate data, and the double logarithmic curve is smooth. Piecewise fractal dimensions are close. The outer interpolation method is used to calculate the fractal dimension of the next point and then back calculate the vertical displacement. The relative errors are calculated by comparing the forecast values and monitoring values, and the maximum relative error is 5.76%. The result shows that the fractal theory is suitable to use in the forecast of the deformation and the accuracy is good.

Keywords

Brick-Concrete Building, Real-Time Monitoring, Fiber Grating Sensors, Constant Di-mension Fractal, Variable Dimension Fractal, Log-Log Line, Prediction

Share and Cite:

Yang, C. , Zhao, X. , Yao, Y. and Zhang, Z. (2016) Application of Fractal Theory in Brick-Concrete Structural Health Monitoring. *Engineering*, **8**, 646-656. doi: 10.4236/eng.2016.89058.

1. Introduction

In China, the structure is generally divided into brick-concrete building, post and panel structure, and reinforced concrete structure, and these buildings during service are bound to produce cumulative damage affected by corrosion, fatigue, aging and other factors, so it is particularly important to monitor the buildings which are on active service.

Health monitoring is an important means to understand the situation of the buildings in use and to layout reasonable monitoring position; analyzing and processing monitoring data will be a key step to master the state of buildings in use; reasonable data processing and effective monitoring models can help staffs to discover abnormities and they can take appropriate measures to ensure the security of the persons and property within the building [1] - [3] . With the progress and mutual integration of modern testing, analysis technics, computer technology, mathematical theory and wireless communication technology, and the traditional monitoring methods are changing to an online, dynamic, real-time direction [4] [5] . Fiber grating technology applying on-line monitoring is a major breakthrough in the field of civil engineering structures or buildings, it has aroused widespread attention [6] - [9] .

Fractal theory means the parts in some way are similar to the whole, under normal circumstances it can be regarded as the state of gathering of fragments. It generally has the following characteristics: 1) fractal sets have a ratio of the details of any small scales, or have a fine structure; 2) fractal sets have some self-similar forms, they may be approximate self-similarity or statistical self-similarity; 3) the fractal dimension of fractal sets is strictly greater than its corresponding topological dimension.

The remote monitoring and warning system used in the experiment includes: fiber sensing systems, signal acquisition and transmission systems, data processing and monitoring and warning system. Fiber grating sensor system includes: types of fiber grating sensors, modulation system and installation of fiber grating sensors. The system of signal transmission and collection includes a correction of fiber grating sensors, application of module, storage structure and methods of vast amounts of real-time data. Data processing, monitoring and warning system is a key part of this experiment, including visualization system of data analyzing and structure running status, and the function of disaster early warning. This study is based on the fractal theory, using the methods of constant dimension fractal and variable dimension fractal to deal with the data collected by fiber grating sensors, and we can predict the vertical displacement of the next point in time, and then to achieve the goal of monitoring and early warning.

2. Constant Dimension Fractal and Variable Dimension Fractal

At present, the application of constant dimension fractal is described by Equation (1)

(1)

Here: r is the characteristic linearity; N is the function associated with r; C is undetermined constant; D is the dimension. Because D is a constant, Equation (1) in log-log line is a straight line, so any two data points, Can determine D and C of the Equation (1) as follows:

(2)

(3)

If there is a negative number in the logarithm operation, all the values of this sequence plus a constant to eliminate the impact of negative number. However, in the curve of log-log line, if there is a nonlinear function, this constant dimension fractal cannot be dealt with. Variable dimension fractal can be introduced to solve the problem, specifically as follows:

Because the fractal dimension D is a function of the characteristic linearity r:

(4)

Then a Function relationship between N and r can be described by

available variable dimension fractal form, , we can obtain that:

(5)

That is a form of variable dimension fractal.

We can know from the Equation (5), any functions the same as can be translated into constant dimension fractal forms, however, in practical engineering, the function is unknown, only discrete data points. In response to this problem, literature [18] presented that data can be accumulated according to a series of conversions, transformed data always can be dealt with in the method of available constant dimension fractal. First, we should plot the raw data points in a curve of log-log line, and substantially arranged in a sequence, that is:

(6)

Then use the basic sequence to construct other cumulative sequence. If you construct a first order accumulation sequence, here, , , , , , similarly we can construct an S-order cumulative sequence. Such as:

(7)

and. Then we build variable dimension fractal model of cumulative sequence of each order, in terms of fist order accumulation, in the log-log line coordinate, the individual data points are connected in turn, so we can obtain piecewise variable dimension fractal model. Finally, choose the best conversion in the piecewise variable dimension fractal model and calculate the fractal dimensions of the subsections, then select a best broken respective line, then we use the interpolation method to calculate fractal parameters need to be predicted of each subsection, finally we anti-derived the data need to be predicted by the Equation (2).

3. Monitoring General Situation about Brick-Concrete Structure

3.1. Monitoring Purpose and the Arrangement of Measuring Points

The test takes the telecommunication building of Hebei University as research object. The telecommunication building belongs to brick-concrete building, 6 layers, 5 layers of main building, built in 1973.12-1976.12, parts of beams, columns exists aging, corrosion and other phenomena. Damage of the aging, corrosion place can easily occur in the future, the main building appears minute vibrations, deformation under the environmental loads, then the vibrations and deformation may lead to crack development, even worse, the whole building may collapse. To make sure the safety of the whole building, teachers and students, we analyze the status of the telecommunication building, then make sure the physical types and the appropriate sensor type and the sensor location.

In the outer wall surface of each floor of typical aging parts, we put FBG surface crack meters to monitor the development of main cracks. In the southeast, northeast, southwest and northwest corners of the main building roof, we install a FBG fiber level to monitor the vertical deformation of main building under outside interference. This is because the top of the building is the most sensitive to external factors, and it seems inconspicuous to artificial disturbance. In the typical beams, columns of the building, we arrange FBG strain gauge to monitor the strain of the beams and columns under outside interference, monitoring point arrangement is as shown in Figure 1, each monitoring instrument parameters are as shown in Table 1 (instrument parameters), the monitor-

Figure 1. Structure model and arrangement of measuring points.

Table 1. Instrument parameters.

ing devices are as shown in Figure 2 (Measuring device).

3.2. Data Analysis

Due to the huge amount of test data, the test is in order to deal with the level monitoring data, we cut out 30 s data of vertical displacement from the northeast corner of the telecommunication building roof, we cut out a data point every second, a total of 30 data points, we take these points as the research object, then we numbers them in chronological order, we use the former 20 points to build prediction model, then use the latter

(a) (b)(c) (d)

Figure 2. Measuring device. (a) roof level; (b) speed fiber grating demodulator; (c) strain gage; (d) crack meter.

10 points to check the correctness of the prediction model.

Table 2 shows that: this part of the vertical displacement includes positive number and negative number, however, the negative number will be unable to operate in the logarithmic coordinates, then we plus 0.2 for them all to eliminate the impact, the processed data is shown in Table 3 (after processing).

The data after processing can obtain piecewise fractal dimension of monitoring data according to Equation (2), Table 4 (Piecewise fractal dimension of monitoring data):

We build log-log coordinate according to the data in Table 4 (Piecewise fractal dimension of monitoring data), then draw the in the log-log coordinate, we can see from the Figure 3 (The log-log curve of the original monitoring data): log-log curve has a big fluctuation, piecewise fractal dimension (D) includes negative number and positive number, so it is difficult to predict.

So we deal with the original monitoring data by first-order accumulation, depending on Equation (7), then we obtain the piecewise fractal dimension (Table 5 the monitoring data of first-order accumulative piecewise fractal dimension). Draw in the log-log coordinates (Figure 4, the monitoring data of first-order accumulative double logarithmic curve),we can see in the Table 4 (Piecewise fractal dimension of monitoring data): the original complex curve change into a relatively smooth curve, each of the piecewise fractal dimension seems similar, so we can predict unknown piecewise fractal dimension according to the known piecewise fractal dimension, then we can anti-derived displacement, this will achieve the purpose of early warning.

Table 2. The original data of northeast.

Table 3. After processing.

3.3. The Prediction on of Monitoring Data

By comparing Figure 3 (The log-log curve of the original monitoring data) and 4 (the monitoring data of first-order accumulative double logarithmic curve), a cumulative fist-order log-log curve (fractal dimension curve) can act as a predictive model to predict the data of the telecommunication building, and using equations to predict the 10 values in the next time. Specific methods are as follows:

1. Figure out the total increment by Table 4 (Piecewise fractal dimension of monitoring data), so the average of the neighboring piecewise fractal dimension is.

2. Figure out the piecewise fractal dimension after the19th subsection.

(8)

Table 4. Piecewise fractal dimension of monitoring data.

Figure 3. The log-log curve of the original monitoring data.

Table 5. The monitoring data of first-order accumulative piecewise fractal dimension.

Figure 4. The monitoring data of first-order accumulative double logarithmic curve.

3. depending on the equation we can obtain:

(9)

We can predict the displacement of the sequence (21 ~ 30), substituting D of Equation (8) into Equation (9). According to the result, we can discover that the relative error is between −5.74% and +5.76% (Table 6, the prediction results of variable dimension fractal). So the method of variable dimension fractal can predict the structural deformation.

4. Conclusion

The result of the test shows that FBG sensing technology can achieve the goal of the remote real-time dynamic prediction to the deformation and displacement of the brick- concrete buildings. Through processing the displacement-time graph, we can visually monitor the state of buildings. Health monitoring data usually presents self-similarity and satisfies the conditions of application of fractal theory. Fractal theory can make a reasonable assessment quickly for the health status of the buildings which are in use after analyzing the dimension changes of displacement curve. When the range of the measurements and time changes, there is no need to change the prediction model, and the similarity of systematic measurements of the brick-concrete structures can be reflected. Displacement data which FBG sensors collect meet the fractal characteristics, but D, piecewise fractal dimension, has a big fluctuation, then variable dimension fractal can be a predictive model to monitor brick-concrete buildings, and the relative error between predictive value and true value ranges from −5.74% to +5.76%, so accuracy of the prediction is better than others. By setting the alarm value of the building, fractal theory provides a new type of monitoring, early warning methods for the practical engineering. Related conclusions have yet to be studied further.

Table 6. The prediction results of variable dimension fractal.

Conflicts of Interest

The authors declare no conflicts of interest.

[1] | Li, H.-N., Gao, D.-W. and Yi, T.-H. (2008) Advances in Structural Health Monitoring Systems in Civil Engineering. Advances in Mechanics, No. 2, 151-166. |

[2] | Zhang, C.-D. and Yang, W. (2009) Research on Buildings Health Diagnosis. Construction Management Modernization, No. 5, 371-374. |

[3] | Qin, Q. (2000) Health Monitoring of Long-Span Bridges. China Journal of Highway and Transport, No. 2, 39-44. |

[4] | He, H.-X., Yan, W.-M., Ma, H. and Wang, Z. (2008) Review and Prospect of Standardization of Structural Health Monitoring System Design. Journal of Earthquake Engineering And Engineering Vibration, No. 4, 154-160. |

[5] | Zhang, Q.-W. (2001) Conception of Long-Span Bridge Health Monitoring and Monitoring System Design. Journal of Tongji University (Natural Science), No. 1, 65-69. |

[6] | Jiang, D.-S. and He, W. (2002) Review of Applications for Fiber Bragg Grating Sensors. Journal of Optoelectronics Laser, No. 4, 420-430. |

[7] | Zhai, Z.-F. (2005) Study on the Application of Fiber Grating Sensing Technique to Health Monitoring for Space Truss. Zhejiang University, Hangzhou. |

[8] | Xiang, L.-Q. (2006) Experiment Study on FBG in Structural Health Monitoring. Dalian University of Technology, Dalian. |

[9] | Morey, W.W., et al. (1989) Fiber Optic Bragg Grating Sensors. Proceedings of SPIE, 1169, 98-107. |

[10] |
Mandelbrot, B.B. (1967) How Long Is the Coast of the Britain? Statistical Self-Similarity and Fractional Dimension. Science, 156, 636-638.
http://dx.doi.org/10.1126/science.156.3775.636 |

[11] | Sun, H.-J. and Zhao, L.-H. (2005) Creation and Application of the Fractal Theory. Journal of Liaoning Institute of Technology, No. 2, 113-117. |

[12] | Qin, P. and Qin, Z.-H. (2010) Forecasting Model of Monitoring Data of High Rock Slope Based on Proved Variable Dimension Fractal Theory. Hydro-Science and Engineering, No. 1, 90-94. |

[13] | Jiang, D.-X., Huang, W.-H. and Xu, S.-C. (1996) Fractal Geometry and Its Application in Rotating Machinery Fault Diagnosis. Journal of Harbin Institute of Technology, No. 2:, 27-31. |

[14] | Qian, S.-H., Ge, S.-R. and Zhu, H. (2005) Fractal Theory and Application in Mechanical Engineering’s Fields. Coal Mine Machinery, No. 6, 123-125. |

[15] | Luo, J., He, L.-M. and Chen, C. (2006) Wavelet Fractal Technology and Its Application to Aeroengine Fault Diagnosis. Journal of Projectiles, Rockets, Missiles and Guidance, No. S4, 862-864. |

[16] | Shi, W.-F. (2007) An Analysis of Fractal and Chaotic Oscillation of Two Marine Generators Connected in Parallel. Journal of Harbin Engineering University, No. 9, 960-965. |

[17] | Jiang, S.-F. and Su, Y. (2009) Fractal Theory And Its Application in Civil Engineering. Engineering Mechanics, No. S1, 148-152, 162. |

[18] | Jin, Y.-Q. (2006) Application of Fractal Theory to Analysis of the Observed Data of Dams. Journal of Hefei University of Technology (Natural Science), No. 11, 1430-1432. |

Journals Menu

Contact us

customer@scirp.org | |

+86 18163351462(WhatsApp) | |

1655362766 | |

Paper Publishing WeChat |

Copyright © 2022 by authors and Scientific Research Publishing Inc.

This work and the related PDF file are licensed under a Creative Commons Attribution 4.0 International License.