^{1}

^{2}

Characteristic analysis of transient electromagnetic disturbance data is very important. In this paper, the time-domain and frequency-domain characteristics of transient electromagnetic disturbance caused by switching operations in substations are analyzed. Two methods are adopted in time-domain analysis. One method is histogram and the other one is normality test. An appropriate procedure for the normality test is proposed. Furthermore, the method used in frequency- domain analysis is to obtain overall envelope. These statistical characteristic analysis methods are showed to be of great value in analyses of the measured samples. The simulation results showed that these methods are effective.

With the increasing requirements of the electromagnetic environment, electromagnetic compatibility problems have become the focus of research in electrical and electronic field. In power system, the complex and advanced equipment cause electromagnetic disturbance produced a more complex, but the ability of advanced equipment tolerance of electromagnetic disturbance weaker, so the electromagnetic compatibility is an important factor affecting power system safe and reliable production [

With the time domain and frequency domain characteristics of complex electromagnetic transient analysis of time domain characteristics of harassment, is helpful to obtain harassment amplitude changes with the time and frequency domain analysis of characteristics in order to provide evidence for shielding and filtering of the two device, ensure the normal work of its own [

All kinds of transient electromagnetic disturbance quantity substation measure and can be used to evaluate various characteristic parameters, including time domain and frequency domain parameters [

1) Micro pulse rise (fall) time T_{r}: Distance between the instantaneous peak corresponding to the time of the recent peak of 10% and then reached the 90% peak instantaneous time interval, is the peak corresponding to the rise time, fall time of negative peak corresponding to the fall time

2) Micro pulse duration T_{m}: The transient wave: start time and end time.

3) The peak to peak value of U_{m}: The absolute duration positive peak and a negative peak difference.

4) The frequency band width of B_{W}: This article from the perspective of immunity test to define the electric field strength is higher than that of 1 V/m, magnetic field intensity is higher than that of 2.65 mA/m, voltage disturbance is higher than 1 V, higher than the current interference frequency components included in the frequency range of 20 mA.

5) The dominant frequency DF: Interference frequency band width in the range of B_{W} is higher than the reference value, amplitude frequency of 6 dB group.

Analysis of time domain characteristics of transient disturbance can obtain the interference source of strength and polarity characteristics and duration of important information, but also the design of an important basis for immunity test. This section of the micro pulse rise (fall) time, micro pulse duration and peak to peak were analyzed by two methods, one is the histogram statistics, the other is the normality test.

The characteristic parameters obtained by one measurement only, if you want to understand the regularity of multiple measurements to the overall analysis. This section carries on the overall statistics of the transient disturbance sample of all, and then gets the probability distribution and trend.

Transient electromagnetic disturbance data of switching operation has obvious random character. If by the time domain characteristics of the whole distribution information, the time domain characteristics can be more accurately grasp the transient disturbance data. The assumption that the distribution of the sample overall, suppose through the validation of the test method, the most common is the assumption of normality assumption. For transient electromagnetic disturbance in the substation switching operation caused by, no literature clearly points out that whether the data obey the normal distribution, so in the test of normality is very necessary.

There are several kinds of normality test methods applied to engineering. According to the design process of testing different applications need reasonable, balance each method and integration. The analysis of this paper should be used.

The normal probability paper test is rough but very convenient, which can be directly on the sample to give an approximate evaluation. According to the graphic trend function transformation corresponding to the sample, it is suitable for the preliminary test. W and D tests are parallel methods, which can be used one according to the real application [

This section of the measured data of characteristic parameters was carried out on the normality test.

The analysis method of this section is to put all the transient disturbance data were carried on the spectrum analysis, and then put them together, for the spectrum amplitude of each frequency point maximum, 80% large value of envelope and 50% large value envelope.

From

Density decreases obviously, in the 100% envelope energy density is the biggest, the band has been expanded to 15 - 50 MHz, the frequency domain analysis of transient electromagnetic disturbance is very important, in every switch operation, due to the measurement disturbance level.

This work is supported by the Fundamental Research Funds for the Central Universities of China under grant 13QN01 and the National Natural Science Foundation of China under grant 51407072. The authors wish to express their gratitude to the editor and the anonymous reviewers.

Xin Wu,Shu Li, (2015) Characteristic Analysis of Transient Electromagnetic Disturbance Data in Substation. Journal of Computer and Communications,03,102-106. doi: 10.4236/jcc.2015.35013