The Loading Capacity of the Elands River: A Case Study of the Waterval Boven Wastewater Treatment Works, Mpumalanga Province, South Africa

Nutrient loads into water resources continues to be a major problem in Southern Africa. This has resulted in significant compromises in the ecological integrity of freshwater resources. The study aimed to assess the pollution load into the Elands River in terms of nitrates and orthophosphates. These variables were compared against the Crocodile Catchment Interim Resource Quality Objectives to determine compliances or non-compliance of the Waterval Boven wastewater treatment plant. Generally upstream nitrate levels did not exceed the ideal limit of 0.5 mg·l −1 as indicated in the 2015 to 2016 samples where values ranged between 0.32 mg·l −1 and 0.27 mg·l −1 , respec-tively. Similarly, observed upstream orthophosphates levels were below the ideal limit of 0.03 mg·l −1 . However, downstream values of both nutrients exceeded the respective set limits. The nutrient load contribution from the sewage plant was characterised by a simple point-source model. Patterns of the loads into the river were demonstrated on a load duration curve based on the river which equalled or exceed 0.18 m 3 /s upstream and 1.31 m 3 /s downstream at 90% of the time. However, the flows were regarded as significantly low to deal with uncontrolled pollution loads. Most of the observed loads fell below the ideal limit of 0.05 mg·l −1 for nitrates both upstream and downstream of the sewage plant. For orthophosphates,


Introduction
The global availability of freshwater is facing numerous threats. These threats emanate from various factors, such as the uneven distribution of rainfall, increased population demand, increased economic demand and mostly uncontrolled pollution into water resources [1] [2] [3] [4]. It is believed that uncontrolled pollution poses the most freshwater challenges in Southern Africa. The pollution originates from both point sources such as waste water treatment plants (WWTPs) and non-point sources such as agricultural run-off from land [5]. Hence the first and most readily-achievable step to managing water quality is to properly manage waste water treatment plants (WWTPs) [6].
Studies agree that South Africa is an arid country with relatively little runoff from rainfall events and therefore loads of pollutants from WWTPs disproportionately affect the water quality of rivers with minimal dilution effect [7] [8].
The Department of Water and Sanitation also alluded that nutrient enrichment and microbial contamination in South Africa are generally associated with water resources that receive large volumes of poorly-treated sewage [9]. [10] concurs that nutrient enrichment, particularly from untreated or partially treated wastewater is very common phenomenon. Several authors do attest that the problem is widespread among developing countries [10] [11] [12] [13]. It is commonly accepted that there is an existing relationship between river flows and water quality. At low flows, there is often a reduced dilution capacity and contaminants easily exceed acceptable threshold concentrations. When low river flows receive high volumes of wastewater effluents from WWTPs or feeder tributaries there is a significant decline in water quality status [8]. As stated by [14], there is often a link between river health problems and flow regimes.
Several models have been developed to determine the pollution loading into water resources. One of the models is the Load Duration Curve (LDC) which was developed to determine the relationship between water quality and water flow. Researchers have been able to use the LDC as an analysis tool to investigate the current and future impact of nutrient load into rivers [15] [16].

Materials and Methods
The Elands River traverses quaternary X21G of the Crocodile East catchment, on coordinates 25˚38'8.18"S, 30˚20'31.22"E. It passes near the town of Waterval Boven before it confluences with the Crocodile River ( Figure 1). The study focused on the Waterval Boven wastewater treatment plant which is located on the southern part of the town (coordinates 25˚38'10.26"S, 30˚20'35.38"E) and services the town and its surrounding townships. Journal of Water Resource and Protection

Water Quality
The study used historical water quality data from 2008 to 2016, obtainable from the Department of Water and Sanitation (DWS) and the Inkomati-Usuthu Catchment Management Agency (IUCMA). The data had been collected according to the guidelines as described by the American Public Health Association [17] and Department of Water Affairs & Forestry [18]. The monitoring points are situated upstream, at the discharge point and downstream of the WWTP on the Elands River.
Water quality results were compared to the Crocodile Interim Water Quality Resource Objectives (RQOs) and the recently gazetted Inkomati resource quality objectives [19]. Whilst the recently gazetted objectives may not cover all parameters of concern, the gaps were addressed by the National Target Water Quality Guidelines (TWQG) [18].

Water Quantity Data
The study used historical monthly flow data from 1957 to 1999 from the DWS gauging stations X2H011 (upstream of Waterval Boven WWTP) and X2H015 (downstream of Waterval Boven WWTP). The data was used to establish the flow regimes along the Elands River and to formulate the necessary graphs, namely; Flow Duration Curve and Load Duration Curves. Data was then analysed based on seasonal patterns (wet or dry periods) [20].

Flow Duration Curve (FDC)
The FDCs were generated using the river flow data, which was sorted in a de-Journal of Water Resource and Protection scending order and ranked according to flow values in Ms Excel. The exceedance probability for each daily flow was computed using the following formula in Equation (1): (1) P = the probability that a given flow will be equalled or exceeded (% of time) M = assigned rank number n = the total number of days for period of record [21] [22].
The FDC was plotted with calculated P values on the X-axis (% equalled or exceeded) and corresponding flow values on the Y-axis (m 3 ·s −1 ).

Load duration curve (LDC)
The load duration curves were developed using the P values calculated from the FDC Loads corresponding to a water quality limit were plotted in kg·day −1 .
The loads of the LDC are calculated based on the formula: Load water quality limit conversion factor Q = × × (2) where Q is daily flow (m 3 ·s −1 ), the water quality limit would typically be a concentration (mg·l −1 ) and the conversion factor would be to convert between the concentration, volume and time units to derive the load in kg·day −1 . For Q in (m 3 ·s −1 ) and water quality limit in mg·l −1 , the conversion factor would typically be 60 sec × 60 min × 24 h × 1000 l/1000,000mg. The LDC is constructed by plotting the P values (%) derived from (1) on the X-axis and load values derived from (2) on the Y-axis [16].

Point-Source Modelling
The nutrient load contribution of the Waterval Boven WWTP was characterised by a simple point-source model based on the model by [23]. Conceptually, the model is based on the fact that effluent flow and nutrient concentrations from any identified point source in South Africa appear to be random over time, which could be related to inconsistent management of WWTPs in South Africa.
where Q psim_i is the point source effluent flow for day i. C psim_i is the point source nutrient concentration for day I , and RAND is a random number between 0 and 1, with independent random numbers being generated for Equations (3) and (4).
The instream simulated nutrient concentration which can be compared to observed data and then be calculated as: where C sim_i represents the simulated instream nutrient concentration (mg·l −1 ) on day i and Q i represents the total flow in the river (m 3 ·s −1 ) on day i. The model is implemented in Microsoft Excel. The values of Q pmax and Q pmin and C pmax and C pmin are manipulated manually until the simulated nutrient concentrations show a similar trend of decreasing concentration with increasing flow (dilution) as evident in the observed data and the values of these parameters can be guided by any information available for a particular point source such as monitored effluent flow or nutrient concentration and WWTP treatment capacity.

Data Analysis
Water quality data was populated and analysed using Microsoft Excel. Graphs showing patterns of the water quality status of the study area were produced and assessed against the Crocodile River Catchment's interim resource quality objectives [24]. Annual averages and standard deviations for each parameter were computed.

Results
The Crocodile Interim Resource Quality Objectives, Target Water Quality Guidelines and Inkomati Resource Quality Objectives (RQOs) were considered for discussions.

Nitrates
The nitrates limits used in this discussion are indicated in Table 1.

Orthophosphate
Orthophosphate values were compared to the standard limits as indicated in Table 2 to determine previous compliances on the Elands River.

Flow Duration Curve (FDC)
The FDC shown in Figure 4 displays the cumulative frequency of flow data from 1957 to 1998. Hence the study noted that at 50% of the time, the flow equalled or exceeded 3.8 m3/s, which presents more than a 100% increase compared to the upstream flows. ing curves; Boundary 1 (Ideal standard limit), Boundary 2 (Acceptable standardlimit) and Boundary 3 (Tolerable standard limit). Figure 6 shows that most of the observed data fell below the ideal limit of 0.05 mg·l −1 for nitrates. There were few instances where exceedances plotted above the ideal limit as much of the loads fell below the acceptable limits of 2 mg·l −1 .

Load Duration Curves
For example, at the 2nd percentile, loads of 492 kg/day were recorded above the "ideal boundary" limit. Whilst at the 50th percentile about 10 kg/day of loads were observed. A significant percent of the time, particularly during low flows, the majority of loads were below 10 kg/day and laid below the ideal limit target.
The Inkomati Catchment Management Area's resource quality objectives were essentially met.
The downstream point essentially takes into consideration the impact of the sewage plant as the main source of pollution (see Figure 7). Overall, much of the observed data plotted below the ideal limit curve of 0.05 mg·l −1 for nitrates.
However, there were few observed exceedances especially during low flows. The observed data exceeding the ideal standard limit curve was however plotting below the acceptable limit curve of 2 mg·l −1 . At the 10th percentile (high flows), 422 kg/day of nitrates loads were observed. There were few instances of observed loads that exceeded the ideal limit during low flows, such as a load of 478 kg/day which was observed in the 67th percentile (low flow period). Since most of the observed loads indicate results that are below the acceptable limit curve, such results were regarded as compliant to standards. Figure 8 and Figure 9 show the loading capacity for orthophosphate upstream and downstream of the WWTP, respectively. The observed loads plotted above the 0.03 mg·l −1 limit (ideal boundary limits) in most cases particularly during low flows. As indicated in Figure 8, heavy loads of 30.9 kg/day were ex-Journal of Water Resource and Protection perienced at the 1st percentile. However at the 90th percentile, approximately 0.37 kg/day of orthophosphate was received. When the loads were plotted against the national target water quality guidelines (TWQG) of 0.025 mg·l −1 , they were plotting above the curve. However, most loads were below the tolerable limit curve of 0.1 mg·l −1 .
The study demonstrated that a significant amount of the observed orthophosphate loads downstream of the sewage plant plotted above the curves/limits ( Figure 9). This means that the orthophosphate loads exceeded the limits most of the time. For example at the 90th percentile, loads were estimated at 19.4 kg/day and were plotting above all the curves. Compared to the upstream loads, where in most cases they plotted below the tolerable limit, the downstream loads were exceedingly above the tolerable limits. Whilst between the 1st and 20th percentile, loads plotted below the tolerable limit curve, although the loads were often above the acceptable limit. Thus, at 30% to 100% of the time, most of the observed loads were plotted above all the limits.

Discussions
The results indicate that the management of loading of the nutrients into the river during periods of low flows is critical.

Nitrates
Nitrates were expected to be lower upstream of the WWTP, however the con-

Orthophosphates
High concentration of orthophosphate in a river often points to the presence of organic waste material [26] [27] [28]. However, overall the orthophosphates concentrations at the upstream point ranged within the tolerable levels. The

Flow Duration Curves
The study area experiences both dry and wet seasons, whereby the dry season takes place from April to October and wet season from November to March. The observed flow data indicates that extended periods of low flows are not uncommon in the Elands River basin (Figure 4). Majority of the time the river flows are generally low, whereby 5% of the time, the flow barely exceeds 5 m 3 /s. Therefore, any inflow of pollutants will have a significant effect on water quality, particularly during low flows.

Load Duration Curves
Instantaneous loads were calculated based on historical water quality data of the Elands River and the daily average flow data, as indicated in Figures 6-9. All the loads that plotted above the load duration curve indicated an exceedance of the water quality objectives whilst those that appear below the curve indicate compliance to the limits.
Nitrates loads upstream plotted below the curves which imply that there were few incidences of exceedances ( Figure 6). Much of the observed data fell below the ideal limit of 0.05 mg·l −1 for nitrates. This indicates that the upstream area is less impacted as there are few sources of pollution, particularly, there are limited land use activities taking place. The downstream nitrate loads showed a considerable amount of observed nitrate loads which plotted below the curves indicating few incidences of exceedance (see Figure 7). However, the few observed exceedances during low flows might suggest an influence of a point source; in this case, it could be the sewage plant. Much of the observed loads complied with the "acceptable" limit graph.
The observed orthophosphates loads exceeded the 0.03 mg·l −1 boundary limits in most cases particularly during low flows. This might suggest a constant point source of phosphate content upstream of the plant. However, most loads were below the tolerable curve of 0.1 mg/l. Hence continuous loads might have a further negative impact on the water resource. However, the orthophosphate loads observed downstream of the sewage plant plotted above the curves (see Figure   9). Even during high flows, observed loads plotted above the ideal and acceptable loads. Therefore, the threat of eutrophication is significant downstream of the sewage plant. If the river continues to receive such loads, it might be rendered non-beneficial to downstream users.

Conclusions
The overall loading capacity of the river, at the area of concern, showed that flows and pollutant concentrations are very variable. Hence it is important to define water pollution and compliance status based on the flow regime at each season. Continuous water resource flow monitoring and water quality sampling are therefore essential to reliably determine the allowable loading pattern into water resources. Furthermore, water RQOs must not be generic. Instead, objectives must address each flow regime. Whilst in other cases data availability is a challenge, this study indicated that knowing the stream hydrology and loading rates is important for water users to easily determine the level of impairment to water bodies.
The loading capacity with regards to the two nutrients can be considered quite varying. Most literature consider orthophosphates as very critical in vegetational growth and the subsequent eutrophication hence much focus may be on the orthophosphates. Therefore, controlling the phosphate loading into the Elands River might play a major role in reducing future eutrophication.