Design of Industrial Water Cooled Chiller for Recycle Cyclohexane in Polyethylene Plant

The research was aimed at providing water for cooling recycled cyclohexane in polyethylene plant to 15 ̊C. This research could be redounding to the benefit of polyethylene plants that are using solution based polymerization technique. A chiller unit of 630 T, which has compressor power input of 378.33 kW and can provide chilled water capable of cooling recycle cyclohexane to 15 ̊C, was designed using Aspen Hysys version 7.1. Four different refrigerants were tested to know the best fit refrigerant for the design and the best among them was R134a. The designed chiller has a coefficient of performance of 6.3 and a capacity greater than that of the defective chiller (550 TR). Unlike the defective chiller, with the increased cooling capacity and corresponding increase in compressor power from 296 kW to 378.6 kW, it could discharge chilled water capable of cooling recycle cyclohexane from 38 ̊C to 15 ̊C without tripping of the unit. With this design, ethylene absorption rate could increase to 40 T/h. Evaporator and condenser were designed and duties were 2166.39 KJ/sec and 2544.72 KJ/sec respectively. A thermostatic expansion valve with flow coefficient of 46.17 gpm was designed. The designed suction and discharge pressure were 414 kpa and 1053 kpa respectively while condenser temperature of 40 ̊C was used for the design. The cooling of recycle cyclohexane from 38 ̊C to 15 ̊C using the chilled water supplied by the designed chiller was simulated using Aspen Hysys.


Introduction
Polyethylene production can be achieved using solution based polymerization technology [1], slurry method [2] or gas phase technology [3].In solution based method, a solvent is used to absorb ethylene and this solvent does not take part

Methods
To achieve the aim of this research, Aspen Hysys software, version 7.1, which used the principles of mass & energy conservations, principles of heat transfer and Thermodynamics to generate results, was used.A design tolerance of 10% was used in this work and a steady state simulation and design procedure was applied.The following assumptions were made: 1) Potential and kinetic energy effect were negligible 2) Evaporator and condenser were at constant pressure 3) Evaporator outlet was saturated vapour while condenser outlet was saturated liquid 4) The vapour compression cycle was at steady state.

5) Adiabatic process occurs at the expansion valve
6) The chiller was considered to be an ideal vapour compression refrigeration cycle and thus, the compression process was isentropic.indicates the refrigeration loop.At evaporator, water used in cyclohexane cooling loss heat to the refrigerant and return to the plate heat exchanger as chilled water at a lower temperature for cooling the recycled cyclohexane while the refrigerant gain heat and vaporized.The compressor lifts the refrigerant to the condenser with increase in energy.At the condenser, the heat removed from the water at evaporator is rejected and the condensed refrigerant is sent back to the evaporator through metering device to complete the vapour compression cycle.

Chiller Water Process Parameter Requirement
The process of cooling 200 T/hr of cyclohexane from 38˚C to 15˚C was simulated using Aspen Hysys to determine the volume of water and the temperature of water going to chiller as shown in Figure 1.The sensible heat of the cooling process was estimated as follows [4]: ( ) where, Q s is the rate of heat loss by the hot cyclohexane, m s is the mass flow rate of cyclohexane, Cp s is the specific heat capacity of cyclohexane at mean temperature, t so is the temperature of cyclohexane after cooling and t si is the inlet temperature of cyclohexane.
In other to estimate the water requirement, energy balance on the plate heat exchanger was done: ( ) where, t wo is the temperature of the water returned to the chiller evaporator after cyclohexane cooling, which is to be determined (as shown in Figure 1) and t wi is temperature of the chilled water with a value not greater than 15˚C.

Selection of Refrigerant
Simulation of the vapour compression cycle and cyclohexane cooling were done at evaporator temperature of 5˚C, 8˚C, 10˚C, 12˚C, & 13˚C to respectively to determine the refrigerant that will require least energy input in the compressor.

Chiller Design
Using the cyclohexane cooling simulation results, the cooling load of the chiller was calculated using Equation (3) [5].
( ) The cooling load was converted to chiller capacity in refrigeration tons (TR) using a conversion factor of 1 TR is 3.5 kW [6].
The ideal P-h diagram for the chiller is shown in Figure 2. It was used to determine the thermodynamic properties of the refrigerant at stage 1 (compressor suction), stage 2 (compressor discharge), stage 3 (condenser outlet) and stage 4 (expansion valve outlet/ evaporator inlet.

1) Compressor Design
Since the compression process is isentropic, the discharge temperature was calculated using the temperature variation between stages in isentropic process.
In this work, the discharge temperature does not exceed 107˚C because the discharge temperature should be less than the critical temperature of refrigerant [7].
Using Figure 2, the compressor energy input could be determined as follows From the definition of enthalpy, Equation (5) could be transformed as [8] ( ) To determine the isentropic efficiency of the designed compressor, isentropic head was estimated as [9] ( ) To get T rev , the compression was assumed reversible and the entropy of isentropic process was zero [4] ( ) The isentropic efficiency of the compressor was calculated using Equation (9) while the compressor power was estimated using Equation ( 10) [10].Advances in Chemical Engineering and Science ( ) In this study, an isentropic efficiency range of 70% -85% was used [9].

2) Evaporator and Condenser Design
The chiller was designed using a condenser temperature of 40˚C and evaporating temperature of 10˚C.The type of evaporator designed was flooded water-cooled shell and tube heat exchanger [11].The tube side fluid was water while the refrigerant, R134a, was the shell side fluid.The condenser was shell and tube.
Taking energy balance on the evaporator, the heat transfer rate can be estimated as shown on Figure 2.
( ) The area of evaporator required for heat transfer was estimated using Equation (12) while the number of tubes was estimated using Equation ( 14) [12].
The log mean temperature difference (LMTD) was evaluated as shown below [11].
Using Figure 2, the heat transferred in the condenser can be established by taking energy balance at the condenser [14].
3) Metering Device At the valve, the refrigerant exists as saturated liquid (f) and saturated vapour (g) due to the flashing action.The dryness fraction of the refrigerant was denoted by "X".To get the dryness fraction of the refrigerant at the valve outlet, the enthalpy of the refrigerant was obtained as [7] ( ) where, h f and h g were gotten from chart (16) From Figure 2, the coefficient of performance of the chiller can be determined as: For this study, the value of COP was considered to be greater than 5.7 since the Carnot COP of the chiller was 5.7.

Solution Technique
The chiller was designed using Aspen Hysys simulator.The following algorithm was developed as solution techniques (Figure 3).

Cyclohexane Cooling Simulation Results
The results of the simulation of the cooling of the cyclohexane are as shown in Table 1.The result suggests that the temperature of water returned to the chiller is 31.65˚C.To cool 200 T/h cyclohexane from 38˚C to 15˚C using 120 m 3 /h of water, the water temperature is 15˚C.This is because the temperature approach of the heat exchanger is 0˚C.A water flow rate of 120 m 3 /hr was used because the maximum rating of the pump supplying water to the chiller is 135 m 3 /hr.

Effect of Evaporator Temperature on Compressor Power
Figure 4 shows how the compressor power input vary with evaporator temperature for all the refrigerants used.It indicates that R134a was the best fit refrigerant for the design since it had the least compressor power input at each respective evaporator temperature.Increased in evaporator temperature from 5˚C through 13˚C reduced the compressor power input for all the refrigerants due to drop in compression ratio which reduced the compressor work as shown in Figure 4.
This effect was maximum when R134a was used; thus, R134a is best fit for the design.
Evaporating temperature of less than 5˚C was not considered to avoid freezing of the chilled water inside the tubes of evaporator; while evaporating temperature greater than 13˚C was not considered to avoid temperature cross.

Effect of Compressor Duty on Coefficient of Performance
Figure 5 shows the effect of compressor duty on coefficient of performance for the different refrigerants used.The best fit refrigerant for the design was 1,1,1,2-tetrafluoraethane (R134a) since it required the least compressor power as shown on Figure 5.A chiller with less power input had high coefficient of performance and is cost effective [6].R134a required a compressor power of 378.1 KW at 10˚C while R152a required 390 kW compressor power at 10˚C since the discharge temperature was higher when R152a was used.Figure 5 also show that the coefficient of performance of a chiller increased with decreased in compressor power because coefficient of performance is the ratio of quantity of energy absorbed in evaporator to the energy input of the refrigeration cycle.R134a has the highest coefficient of performance of 6.49 since it had the least compressor input of 333.6 kW as shown in Figure 5.

Chiller Design Results
The summary of the results of chiller designed is shown in Table 2.The capacity of the designed chiller is 630 Refrigeration Tons.7,799,004 kJ/h of heat could be removed when the chiller water was cooled from 31.65˚C to 15˚C at the evaporator using R134a.Electrical power of 379 kW is needed by the compressor to expand the 42.2 m 3 /h R134a from 10˚C to a designed temperature of 49.53˚C.
The type of compressor is centrifugal because of the high volume of refrigerant that is needed in the vapour compression cycle.

Compressor Design Results
Table 3 shows the compressor sizing results gotten from Hysys.The power input of the designed compressor was 378.6 kw while it had adiabatic efficiency of 75%.The compressor had an adiabatic head of 1995 m.This high power consumption was as a result of increase in evaporator duty and refrigerant flow.The maximum discharge temperature of the designed compressor was satisfactory as it was less than the critical temperature of refrigerant which is 107˚C.The compressor was single stage because the compressor ratio was less than 4.0 [11].

Evaporator and Condenser Design Results
Table 4 shows that a design heat duty of 7,799,004 kJ/hr was required in the evaporator of this vapour compression cycle.The evaporator design temperature was 10˚C.This was because for a flooded water-cooled evaporator, the tempera-Advances in Chemical Engineering and Science ture approach, which is the difference between the evaporating temperature and the chilled water outlet temperature, should be 3.3˚C -5.6˚C [6].The tube side outlet temperature was 15˚C because the design was made at a worse case scenario of a temperature approach of the plate cooler, where the cooling of cyclohexane was done, at 0˚C.
The area of heat transfer was 288 m 2 as compared to that of defective chiller which is 244 m 2 (from vendor diagram) and the evaporator had 764 tubes.This area increase was as a result of the rise in heat duty.
Table 5 suggests that the condenser duty required for the design was 9,167,040 kJ/hr and a condensing temperature of 40˚C was used because as a rule of thumb, the condenser temperature is 10˚C -15˚C above ambient temperature [15].
The overall heat transfer coefficient of the condenser was 3796 kJ/h-m 2 C and the area of heat transfer was 332.5 m 2 as compared to that of the defective chiller that was 319 m 2 .The total number of tubes of the designed condenser was 882.
To avert the effect of corrosion, carbon steel was used for shell design.

Expansion Valve Design Results
Table 6 shows the expansion valve sizing results.For this design, thermostatic expansion valve was considered.The valve has a flow coefficient (C v ) of 46.17 gpm at 50% opening.
The flow rate through the valve was 5.22 × 10 4 kg/h while the pressure drop of the valve was 597.1 kPa.

Comparison of the Propose Designed Chiller with the Existing Chiller
Table 7 gives a comparison of the proposed designed chiller with the old defective one.To cool recycle cyclohexane to 15˚C using the proposed designed chiller, the chiller capacity increased from 550 TR to 630 TR and compressor duty increases from 1,065,600 kJ/h to 1,361,988 kJ/h due to the drop in chiller water temperature which increased the evaporator duty.The compressor power input in the new designed chiller was greater than that of the old chiller because of increased in compression ratio which was as a result of the rise in discharge temperature from 29.3˚C to 49˚C. Figure 6 suggests that when proposed chiller is used, it could give the least outlet temperature of cyclohexane.

Effect of Chiller Capacity
Figure 7 shows the effect of chiller capacity on ethylene absorption rate.The ethylene absorption rate increased from 20 T/h to 35 T/h when the chiller of 550 TR was used.By interpolation, it could be predicted that with the proposed chiller of 630 TR capacity, ethylene absorption rate would increase to 40 T/h as shown in Figure 7.This is because with 630 TR capacity, the cyclohexane would enter the absorption unit at 15˚C and this would reduce the equilibrium absorption temperature of ethylene [1].
Figure 6.Temperature profile of cyclohexane before chiller fault, when chiller was by-passed, and when proposed chiller would be used.

Figure 1
Figure1is the chiller loop with cyclohexane cooling loop.The path "abcd"

a
Advances in Chemical Engineering and Science

Figure 2 .
Figure 2. Ideal P-h diagram for the chiller.

Figure 3 .
Figure 3. Algorithm of the chiller design.

Figure 4 .
Figure 4. Effects of evaporator temperature on compressor power input for different refrigerants.

Figure 5 .
Figure 5.Effect of compressor duty on coefficient of performance for different refrigerants.

Figure 6
Figure6shows the temperature shows the temperature profile of cyclohexane as flow of cyclohexane increased when these scenarios were considered; before chiller fault, when defective chiller was bypassed and when the proposed chiller would be in use.The presence of the chiller caused a temperature drop of up to 23˚C in the cyclohexane used in ethylene absorption when cyclohexane flow was raised to 200 T/h.Cyclohexane was discharged to the ethylene absorption unit at 15˚C.This was because greater heat energy was removed from the cyclohexane by

Figure 7 .
Figure 7. Effect of increase in chiller capacity.

Table 1 .
Process requirement of chiller water.

Table 7 .
Comparison of propose designed new chiller with the present chiller.