Cost Optimization Modeling of Renewable Energy Sources in Smart-Grid Using SCADA

In recent times, renewable energy production from renewable energy sources is an alternative way to fulfill the increased energy demands. However, the increasing energy demand rate places more pressure, leading to the termination of conventional energy resources. However, the cost of power generation from coal-fired plants is higher than the power generation’s price from renewable energy sources. This experiment is focused on cost optimization during power generation through pumped storage power plant and wind power plant. The entire modeling of cost optimization has been conducted in two parts. The mathematical modeling was done using MATLAB simulation while the hydro and wind power plant’s emulation was performed using SCADA (Supervisory control and data acquisition) designer implementation. The experiment was conducted using ranges of generated power from both power sources. The optimum combination of output power and cost from both generators is determined via MATLAB simulation within the assumed generated output power range. Secondly, the hydro-generator and wind generator’s emulation were executed individually through synchronizing the grid to determine each generator’s specification using SCADA designer, which provided the optimum power generation from both generators with the specific speed, aligning with results generated through MATLAB. Finally, the operational power cost (with no losses consideration) from MATLAB was compared with the local energy provider to determine the cost-efficiency. This experiment has provided the operational cost optimization of the hydro-wind combined power system with stable wind power generation using SCADA, which will ultimately assist in operations of large-scale power systems, remotely minimizing multi-area dynamic issues while maximizing the system efficiency. How to cite this paper: Islam, N., Ali, W.H., Kolawole, E.S., Fuller, J., Obiomon, P., Attia, J.O. and Abood, S. (2021) Cost Optimization Modeling of Renewable Energy Sources in Smart-Grid Using SCADA. Communications and Network, 13, 51-67. https://doi.org/10.4236/cn.2021.132005 Received: October 17, 2020 Accepted: May 18, 2021 Published: May 21, 2021 Copyright © 2021 by author(s) and Scientific Research Publishing Inc. This work is licensed under the Creative Commons Attribution International License (CC BY 4.0). http://creativecommons.org/licenses/by/4.0/


Introduction
The increasing energy demand rate places more pressure on the termination of conventional energy resources. Therefore, it has become a significant phenomenon to balance this extensive energy demand by enforcing the proper use of resources that already existed and implementing new resources to optimize the cost accordingly. On the other hand, the depletion of fossil fuels like coal, petroleum, natural gas, etc. is creating an adverse effect on the environment. Global warming, emissions of greenhouse gases, climate change are the negative impact that is associated with nature is being produced by fossil fuel-based energy generation.
Energy management is the energy policy algorithm, planning, execution, and actions to propagate resource conservation, climate protection, and cost savings while sufficient energy demand is being fulfilled. The optimization of using new renewable energy sources connecting with the previous existing resources may cause distinct complications. Cost optimization is the process that attempts to function cost reduction disciplines with the standard pricing, simplifies the platform, and executes the plan/application related to cost for a particular item.
Economic dispatch (ED) defines the system providing the demand load over the appointed units with the lowest power production cost [1]. The dispatch operating department can focus on the indicated aspects to influence the economic dispatch accomplishment procedures, which provides the accomplishment to function and optimize the power system with decent quality, economy, and environmental security protection [2] [3] [4] [5] [6]. Moreover, ED is considered the simplest to formulate on a long-term basis instead of utilizing the power system daily efficiently. To overcome this shortcoming, the investigation of the problem should be not just focused on economic viewpoint but also should direct the question into multiple time intervals with different and interconnected power systems [7]. Regarding these (Multi-Area Dynamic ED) MADED problems, literature [8] illustrated a spectacle for reducing the cost of consumption by assuming the percolation of wind power and pumped storage power plants.
The pumped storage power station has also become the economic peaking power supply because of its flexibility, reliability, and capacity. A combination of wind and pumped storage power plants are considered financial and the solution to this problem. Pumped storage utilization helps to smooth and improve the fluctuations of the combined power generation system of wind and pumped storage power plants. Literature [9] portrays an optimization prototype for wind power plant, which contains the highest efficacy and steady output power with the assigned and the supplied energy leads to the cost reduction of the system [10]. A strategy that helps solve scheduling issues also plays an essential role in making the system economical [11]. The researchers emphasized various facts to improve the load fluctuation, power integration, and cost optimization due to the multiple constraints in applying pumped storage and wind power plant. In the literature [12], the traditional numerical calculation of wind-hydro power stations has approached after a wind load combination to match the equivalent load. Literature [13] illustrated the model to progress the capacity of wind power integration. Furthermore, the reduction of wind power fluctuation is achieved by implementing the improved Bat algorithm that portrayed the pumped storage-wind combined power system [14]. In this literature, the hydro-wind power station's economic dispatch is calculated with a SCADA system considered modern technology. The phenomena of this technology are used to control the power flow from the generators to loads.
The advantage of using the SCADA system is to maintain the microgrid's operating schedule by the smart grid communication technology as PLC. Also, the result obtained from the SCADA system is verified by MATLAB program code.
But the benefit of using the SCADA system is to control the operating schedule remotely, while there is no such technique in MATLAB. Particularly, operation remotely by the SCADA system has been recommended more beneficial as MATLAB lacks this operation. Therefore, a concept has proposed to acquire the solution of these technical problems associated with the Smart Grid network worked as an integral part of the management scheme.

Renewable Energy and Traditional System
Renewable energy is the recollected energy from renewable resources. It can be defined that power and energy generated from different sources like solar, wind, ocean, hydropower, biomass, geothermal resources, and hydrogen originated from renewable resources.

1) Pumped storage Power Plant
The availability of water is an essential requirement for hydropower generation. Hydropower generates both kinetic energy and potential energy. Usually, the water from lakes and the water from reservoirs at an elevated level is the hy-  The generator consists of two converters: MSC and LSC shown in Figure 3. Also, the DC chopper and crowbar play an essential role when faults disrupt the system. When there is a constant wind energy input, the DFIGURE supplies the machine-side converter and generator with reactive power. During a period of disruption in unsteady wind energy, a voltage dip is noted and supplied reactive power can be stabilized through the line-side converter. When the system disrupts with the turbine's faulty power flow, it results in a high generation of energy between the machine-side converter and the line-side. This excess energy flowing from the rotor circuit into the MSC can be harnessed via a DC Chopper. Figure 4 shows the connection of the DC Chopper and crowbar to the DFIGURE that will be connected to the wind turbine.

Transmission Line
The transmission line is a medium to transmit to radiofrequency, voltages. A transmission line is a circuit along with distributed parameters, such as series resistance, series inductance, shunt capacitance, and shunt conductance are distributed along the whole length of the line, as shown in Figure 5.
The d.c resistance of several types of conductors at a specified temperature T is found by: where T ρ conductor resistivity at temperature T (Ω•m) L-conductor length (m); A-conductor cross-sectional area (m 2 ).
It is defined as the flux linkages per unit current,    where ψ is flux linkage (Weber-turns) I is current (amperes); L is a constant of proportionality, inductance (henrys).
Potential difference is the number of charges through two points of a conductor. Usually, the two conductors' capacitance is constant when placed in parallel, but this constant is subjected according to the conductors' size and placement.
The ratio of output power and input power of the transmission line is the transmission efficiency.
Transmission efficiency

Emulation of Renewable Energy Sources in the Smart Grid
The cost optimization model has been executed into several steps in this section.
Step 1: The output power and cost calculation by MATLAB using an incremental cost function.
Step 2: This step has executed three case studies: CASE 1: Dark lamp Manual synchronization to the grid for a pumped storage power plant to determine the pumped storage power plant's specification. CASE 2: Grid synchronization for a DFIGURE to determine the wind power plant's specification.
CASE 3: Connection of hydro generator and wind generator to the grid to verify the MATLAB' stated result.
Step 3: Comparison of the mathematical results to the practical results. 1) Step One: In this experiment, the range is assumed for pumped storage generator output power from P 1min = 10 W to P 1max = 200 W. The range is considered for wind generator output power from P 2min = 10 W to P 2max = 150 W. Therefore, the minimum and maximum generated load power range for the combination of pumped storage power plant and wind power plant system is P Lmin = 20 W to P Lmax = 350 W.
The general cost C is considered as, 2 ;$ h C aP bP c = + + (4.1) (with the consideration of no generator losses and limits) where a, b, and c also represent cost but in constant cost, which will not be considered to optimize in this study, and P is the generated power from the generator. The general cost is a function of output power of each power plant. The incremental cost of the two-power unit is a calculation of the slope of generating power and receiving the units' power curves. This cost helps to determine the optimum combination of power productions that reduces the total energy. Then, incremental cost λ is, The general cost and incremental cost for a pumped-storage power plant is, As the minimum power for both of the power plant is 10 W, and substitute P 1 = 10 W in Equation (4.8) which gives 1 0.00 W h 82 $ λ = ⋅ and substitute P 2 = 10 W in Equation (4.10) which provides 2 It is observed that 1 2 λ λ < , which means that the incremental cost of pumped storage is less than the wind power plant's incremental cost at minimum power generation of 10 W from both power plants. As the incremental cost of the wind power plant is higher than the pumped storage power plant during generating minimum power 10 W, keeping the output power of wind power plant P 2 = 10 W constant for the next step and calculate P 1 = 89 W when the system is in an optimum state, 1 2 1.53 λ λ = = from Equation (4.8). The next steps will continue by assuming various values of the output power of the pumped storage power plant P 1 , to calculate P 2 , P L , and incremental costs at optimum state 1 2 λ λ λ = = . As mentioned before in this section, the maximum power is 200 W for pumped storage and 150 W for wind power plants. The same previous steps will continue to determine P 2 , P L , and incremental cost for assumed various P 1 ; until each power plants reach their appointed assumed maximum power, 200 W for P 1 Figure 7 indicates the characteristics of output power (P 2 ) generated from the wind power plant and the incremental cost λ considering the power range 10 W < P 1 < 150 W. The incremental cost λ is constant when P 2 = 10 W, whereas it starts to act as linearly from 10 W to 150 W with increasing incremental cost λ from 0.882 to 1.53 $/Wh. Figure 8 shows the characteristics of the combined system's load power (P L ) versus incremental cost λ. This curve has three linear parts; first, the curve is linear from 10 to 100 W with increasing incremental cost λ. The second curve is linear from 100 W to approximately 280 W with increasing incremental cost λ, and the third one is linear from around 280 W to 350 W.

2)
Step Two: Three experiments were done in this step. They are given below:      . Set-up for manual synchronization using a "dark-lamp synchronization circuit." A synchronous generator is used as a three-phase synchronous machine.
When the speed is around 1800 rpm, the exciter voltage is 20 V, and consistent voltage is measured as 212 V. All the incandescent lamps started to get dark. The power switch of the synchronization unit has then connected the generator to  Figure 10 shows the connection of the wind generator to the grid. A doubly-fed asynchronous generator is used to control the variability of wind speed.
"WindSim" software is used to emulate the system in real with a servo-machine test.
The generator is synchronizing with the rotor current and is set for a maximum of 0.21 A and frequency 60 Hz and variable speed from 210 to 217 V.
Then, the generator automatically synchronizes with grid parameters.
CASE 3: The combined connection of hydro and wind generators to the grid The synchronization of two renewable power stations together in the SMART-GRID has proposed to observe the optimum power with the SCADA system. This is the following steps of the previous case 1 and case 2. Figure 11 shows that 2 bus-bar systems have been used, where bus 1 is represented as a slack bus. The hydropower plant and wind power plant are connected in parallel to the bus 2. The inductive load is connected through the transmission line.
Usually, the fluctuation rate of output power from the hydro-generator is less than the wind generator's output power. Therefore, DFIGURE is used to generate power in power plants to avoid wind speed variability. Figure 12 indicates the power flow of the system where the regulator helps regulate the generated wind power's viability. Machine-side converters (MSC) and Line-side converters (LSC) are situated to minimize the faults due to wind power fluctuations. The SC-ADA system was used to control the power flow and reach the optimum generated   power from both generators individually, synchronized to the grid. Figure 13 has displayed the schematic diagram of the system. Smart grid made SCADA system implemented, and SCADA contributed as an interface with industrial management. Also, this system is integrated by a soft PLC program.
The SCADA designer's main function is to acquire data from the power plants to control the power plant. Sensors, RTU, and HMI, and the communication unit are the four components to interface with the industrial interface, collect and control the entire system's data (Table 3).
Total power,

Conclusions
This experiment is focused conducted to optimize the cost of power generation Many sectors and specifications can be expanded to improve the cost optimization power system in the future. Connecting three power plants will possibly make a cost-effective plant instead of combining two power plants. Calculating the total cost, including operational cost and installation cost, need to be considered to develop the power system. Power loss may also be explored in the future. Future work can also explore the load curve for annual energy consideration with time. Besides, the capacitor's injecting may improve the power factor that reduces the power system's cost. Furthermore, artificial intelligence methods may be the next step as a genetic algorithm, PSO, to establish a more efficient power system.